- What size wire should I run to my garage?
- Can you put 2 GFCI outlets on the same circuit?
- Is 20 amps enough for a garage?
- How many outlets can be on a 20 amp circuit in a garage?
- What is the difference between GFI and GFCI outlets?
- How far does a GFCI have to be from a kitchen sink?
- How far can you run 12 gauge wire on a 20 amp circuit?
- Should a refrigerator be on a GFCI?
- What is code for outlets in garage?
- Does every outlet in a kitchen need to be GFCI?
- How many outlets should I put in my garage?
- How many outlets can one GFCI protect?
- Can I wire lights and outlets on the same circuit?
- Do all outlets in basement need to be GFCI?
- Can Romex be exposed in a garage?
- Is conduit required for garage wiring?
- Can I replace a regular outlet with GFCI?
What size wire should I run to my garage?
In general, you need 10-gauge wire for a 30-amp subpanel, 8-gauge for a 40-amp one and 6-gauge for a 50-amp subpanel.
If you need a 100-amp subpanel, you’ll be running beefy 3- or 4-gauge cable with a 6-gauge ground wire..
Can you put 2 GFCI outlets on the same circuit?
When you need to wire multiple GFCI outlets such as in a kitchen or bathroom you have a couple of options. To save money, you can put in a single GFCI and then wire additional standard outlets to the “LOAD” output from the single GFCI. This provides the same protection as having a GFCI at each location.
Is 20 amps enough for a garage?
As a general guideline, you’d use 12 AWG copper conductors with a 20 ampere breaker, and 14 AWG copper conductors with a 15 ampere breaker. Since the receptacles are in a garage, they’ll have to be GFCI protected. … Since it’s a garage, I’d install a single 20 ampere circuit at the very least.
How many outlets can be on a 20 amp circuit in a garage?
10 receptaclesOne rule of thumb is to assign a maximum draw of 1.5 amps to each receptacle, which allows for 10 receptacles on a 20-amp circuit.
What is the difference between GFI and GFCI outlets?
There is no difference. Ground fault circuit interrupters (GFCI) and ground fault interrupters (GFI) are the exact same device under slightly different names. Though GFCI is more commonly used than GFI, the terms are interchangeable. GFCI circuit breakers and outlets protect people from electrical shock.
How far does a GFCI have to be from a kitchen sink?
3 feetIt must be a GFCI, and it must be within 3 feet of the edge of the sink. Either behind or beside the sink is acceptable — across from the sink on an opposite wall is not. If the bathroom has two sinks, each must have an electrical receptacle within 3 feet.
How far can you run 12 gauge wire on a 20 amp circuit?
For a 20 amp, you _must_ use 12 gauge to start with, 14 gauge doesn’t handle a 20 amp fuse at all. A 12 gauge wire is typically good for 15 amp at 100 feet.
Should a refrigerator be on a GFCI?
In a dwelling unit (residential), GFCI protection is only required for kitchen receptacles that serve the countertop surfaces. There’s no requirement to GFCI protect receptacles that serve a refrigerator. Unless the fridge is plugged into a countertop receptacle.
What is code for outlets in garage?
As of the 2017 NEC, newly constructed garages need at least one dedicated 120-volt 20-amp circuit that serves only the garage. … Garages must have at least one receptacle, including one for each car space. All garage receptacles must be GFCI-protected.
Does every outlet in a kitchen need to be GFCI?
In kitchens, all outlets that serve countertop surfaces should be equipped with GFCI outlet protection. That would include any outlets on walls, behind wet areas (sinks, etc.) that have features such as countertop breakfast bars (open counter surfaces above sinks used to sit at on the opposite side).
How many outlets should I put in my garage?
Take into consideration any plans for a future workbench ahead of time. It is much easier to add outlets during construction than after the walls are all closed up. It is easy to say one every 6′ on each wall in the garage. That means a 20 x 20 garage would be looking at a minimum of three outlets with that figure.
How many outlets can one GFCI protect?
There’s no limit. A standard GFCI will protect up to 20 amps, drawn from any combination of receptacles, either the built-in one or any number of additional ones connected to its load terminals.
Can I wire lights and outlets on the same circuit?
Basic answer to your question of can a mixture of lights and receptacles be installed on a single circuit is yes. The neutral will be white but some switches are wired up with a white wire that is not a neutral. … As a rule of thumb in counting devices on a circuit you count each outlet (light or receptacle) as 1.5 amps.
Do all outlets in basement need to be GFCI?
2. All basement outlet openings must be protected by a listed combination type Arc-Fault Circuit Interrupter (breaker), except bathrooms and unfinished areas. … All 125-volt outlets in unfinished storage areas must be GFCI protected.
Can Romex be exposed in a garage?
Re: Exposed romex NM cable is permitted to be run exposed on the surface of the building finish. … In a house or a finished garage, electrical cable is protected from damage by permanent wallcoverings like drywall, plaster or even wood, but that’s not the case in an unfinished garage.
Is conduit required for garage wiring?
Many garages contain one or more walls made of concrete or already drywalled. Cable installed on these exposed surfaces has to be protected by conduit. We show EMT (electrical metallic tubing; Photo 7), but you can also use rigid PVC conduit. … Always exit cable through connectors.
Can I replace a regular outlet with GFCI?
You can replace almost any electrical outlet with a GFCI outlet. Correctly wired GFCIs will also protect other outlets on the same circuit. While it’s common to find GFCI outlets in bathrooms and kitchens, there are GFCI outlet requirements.